Air Conditioning Start-up and Seasonal Maintenance Checklist
This convenient Air Conditioning Checklist has been designed to help maximize reliability,
economy, and fuel conservation in the operation of this equipment.
Information from our files indicates that a great many failures take place at start-up or early in the cooling season because of inoperative controls or safety devices. Most of these accidents could have been prevented if a little more attention had been paid to readying the equipment for service or when the equipment was taken out of service at the end of the season. We therefore recommend that the following measures be taken to ensure a trouble-free cooling season and reduce the likelihood of equipment malfunction.
The tips offered here are intended to complement and not replace the recommendation
of the equipment manufacturer. It is recommended that operators consult with their original equipment manufacturer for instructions related to their specific model and operating conditions.
- Energize the crankcase heaters for at least eight hours before start-up and
before taking insulation resistance readings of hermetic motor windings.
Crankcase heaters should be left energized for the rest of the season so
that whenever the compressor is idle, the heater will prevent refrigerant
"migration" to the crankcase.
- Test the lubricating oil for color and acidity, and check crankcase oil level.
- Check the air passages of open motors for cleanliness and obstructions.
- Check the condition of and lubricate bearings.
- Take insulation resistance readings. If the readings indicate less than one
megohm resistance, don't start the motor. Check for the cause of the low
- Inspect starter contacts for deterioration from short cycling, arcing, or
- Check terminal connections for tightness.
- Examine the overload protection for defects, and for proper size.
- Check mechanical linkages for binding and excessive looseness.
- Check timing devices for correct operating sequence.
Operating and Safety Controls
- Determine that the controls are properly calibrated and in working order
particularly thermostatic controls, oil pressure safety switches and flow
- Be sure the circuit is equipped with a moisture indicator and if moisture is
indicated, install new liquid line filter/drier cores. Determine and correct the
source of the moisture.
- Check the expansion valve for proper operation and superheat settings over
the full range of operation.
Condensers and Evaporators
- Ensure that proper cleaning of heat transfer surfaces for the type of unit in use
has been completed prior to operation.
- Cooling towers: Check the baffles for tightness and soundness. Clean the
baffles, sump and the spray nozzles. Check the make-up water valve for
- Check the bearings, packings, shaft couplings, and seals. Lubricate bearings.
- Check for broken, cracked, bent or loose blades. Check hubs, fan shaft and
- Check the belt condition and belt tension.
- Replace air filters.
- Check all piping supports for signs of distress.
- Check for external damage and excessive vibration.
Tips courtesy of The Hartford Steam Boiler Inspection and Insurance Company (©1996-2009)