The following is a brief overview of Electrical Preventive Maintenance for small businesses. This is to be used as an introduction to the topic and a starting place for additional research. Specific questions about this article should be directed to your HSB representative.
Inadequately maintained electrical systems are a leading cause of business interruption, poor energy efficiency, and premature equipment breakdown. A well planned and executed electrical preventive maintenance (EPM) program will reduce equipment failures, unplanned down time and unbudgeted expenditures. Unfortunately, many small businesses do not have the technical personnel experienced with EPM programs. This guide serves as an overview describing the basic components of an effective EPM program.
An EPM program involves working with energized and rotating equipment, a lockout/tagout program and a variety of electrical test equipment. Only personnel properly trained and qualified in electrical work and electrical safety should perform these tasks. All work associated with electrical power systems and equipment should be performed in accordance with appropriate manufacturer's instructions and guidelines and accepted industry practices. The required safety equipment or specialty tools should be determined and should always be readily available.
An EPM Program
An EPM program is simply the scheduled inspection, testing and maintenance of critical electrical components and their support systems. The intent of an EPM program is to identify and address any issues before a failure occurs. For an EPM program to achieve long term success, it must be within available resources, well defined, well understood and properly implemented and documented. To make this happen there are three basic steps required: assess, implement and sustain.
Assess – What is the amount of lost time and product that can be attributed to failures? What in-house technical resources are available? Are one-line drawings of the power system available? Are the critical production components and their support circuits known? What is the age and overall condition of the equipment? These questions should be answered during the assessment stage.
Implement – This step involves both planning and accomplishing the work. The required maintenance activities and frequencies as well as the procedures and schedules to accomplish the work should be documented. An individual should be assigned to oversee the program. Once these steps are completed, the work should be accomplished according to plan and the results documented.
Sustain – The ongoing performance of the program is critical. The program results should be reviewed and be utilized as an input to continuously improve the program.
Technical Components of an EPM Program
EPM programs involve maintenance and testing activities to keep electrical apparatus clean, cool, dry and tight. These activities should be scheduled based on the condition of the equipment, historical information concerning the equipment and the manufacturer's recommendations. If no guidance is available, HSB recommends that electrical preventive maintenance be performed at three year intervals. More frequent maintenance should occur if conditions warrant.
Keep it Clean and Dry
Electrical equipment rooms should:
Electrical equipment should be:
Keep it Cool
Minimize heat buildup in electrical apparatus and in equipment rooms by:
Keep it Tight
Electrical connections should be:
The above suggestions are basic checks and inspections to minimize the most common and frequent problems. However, these checks and inspections do not constitute a comprehensive EPM program. Additional testing and maintenance activities based on a facility's components and sensitivity to down time are required for a complete EPM program. HSB Recommended Practice for Electrical Preventive Maintenance should be reviewed for additional information concerning this subject. Experienced electrical contractors and electrical testing companies are also good sources of information.
It is important to fully understand and appreciate the importance of an EPM program. An effective EPM program will reduce equipment failures as well as unplanned down time. The time and effort to establish, implement and maintain an effective program has proven to be well worth the effort.
|Tips courtesy of The Hartford Steam Boiler Inspection and Insurance Company (©1996-2009)|
Click here to view a printable PDF version.